|ambient temperature||standard 40 °C (up to 55 °C possible)|
|place of production||Germany|
|marine classification||yes (individual inspections)|
|cooling time between 2 starts||standard 30 minutes (up to 10-60 minutes possible)|
|number of consecutive starts from cold||standard 2 ( up to 3 possible)|
|waiting time between 2 consecutive starts from cold||3 × start time|
|The cold condition is achieved after the last start + 4 x cooling time between 2 starts|
|short time power frequency withstand voltage||10||20||28||38||kV - 1 minute (50Hz)|
|rated lightning impulse withstand voltage||40||60||75||95||kV|
|short circuit current||6||8||16||20||25||31.5||40||kA - 1s|
|peak withstand current||15||20||40||50||63||80||100||kA|
|altitude||standard < 1.000 m (up to 2.900 m possible) over NHN|
the start transformer
|description||dry-type, vacuum pressure impregnated with lifting lugs and overvoltage arrestors in the star point|
|cooling||AN (air natural convection)|
|number of tappings||standard 3 (up to 5 possible)|
|insulation class||H (180 °C), used to 150 °C|
|core material||electrical sheet|
|temperature supervision||in each phase 2 PT 100 elements|
|place of production||Germany|
depending on the execution (rated voltage, rated current, short circuit current) a MV vacuum contactor, a contactor with HH fuses or a vacuum circuit breaker will be used.
depending on the execution (rated voltage, rated current, short circuit current) a MV vacuum contactor or a vacuum circuit breaker will be used.
the mains switching device with the motor protection relay is located in the MV distribution and is no constituent of the starter.
|Description||powder coated steel housing with lifting lugs, earthing terminal and earthing bolts at the incoming, suitable for fork lift transportation|
|protection class||standard IP 3X ( up to IP 43 possible)|
|MV cable entry||from below, with cable clamp support|
|LV cable entry||from below|
Dimensions and weights
Dimensions and weight of the starter are depending on the rated voltage, the rated current, rated short circuit current and the start current of the motor. Furthermore the size of the start transformer has a significant influence on the total dimensions. The size of the transformer will also be additonally determined by the start time and the start voltage, which are also related to the data of the driven machine. All our offers contain dimensions and weight of the respective starter.
|The dimensions of the starter range between|
The weights of the starter range between
Large starters are delivered in two units and will be mounted at site (a detailed manual will be provided on this).
|functions / supervisions||start current|
|number of consecutive starts|
|waiting time between consecutive starts|
|achievement of cold condition|
|switch position control for 2 switching devices in the starter and one switching device (mains) outside the starter|
|start transformer temperature|
|control voltage||standard 230 V AC (others are possible), to be provided at site|
|LV-cable cross section||minimum 0,75 mm2|