# Start procedure

The main components of the motor starter are: starting transformer T, By-pass switch B and star-point switch S. The mains switch is located in the MV distribution.

## 01. Before the start

N is open. The motor is standing still.

## 02. Start

B open, S closed, N closed. The motor is started with reduced voltage.

### Transformation provides a lower start current

Compared to other starting methods (electronic soft starter, starting reactor etc.) the mains current is lower than the motor current during the starting process. This results in a lower voltage drop respectively a higher motor torque.

### Example for a calculation:

The DOL starting current of the motor is IDOL = 5 × In (In = motor rated current)

The motor voltage during the start Us is 61% of the rated voltage Un (Us/Un = 0,61).

Therefore the motor current IMot = Us/Un × IDOL × F
(F is a factor depending on the motor)

IMot = 0,61 × 5 × 0,91 = 2,8 × In

### Calculation of the mains current IS:

A transformer has the same power at primary and secondary, which leads to the fact that the products of current and voltage are the same.

Un × IS = Us/Un × IMot => IS = Us/Un × IMot / Un
IS = 0,61 × 2,8 = 1,7 × In
For the other starting methods the following is valid: the mains current IS is equal to the motor current Imot.

IS = IMot = 2,8 × In

## 03. Switch over

N remains closed. S will be opened. Immediately after B will be closed. During the switching over (S already opened, B not yet closed) the starting transformer works as a reactor. This results in a continuous voltage supply of the motor.

## 04. Operation

B closed, S open, N closed. The motor is running with rated voltage.

## 05. Stop

N will be opened. The motor stops. „Start“ „Operation“ ## Any questions?

Do you need support to start your drives? We are here to help. Please contact us.